||Cable for power distribution and power supply stations used in Utility and Industrial applications, for rated voltages up to 18/30kV Suitable for fixed installations, indoor or outdoor, in open air on cable trays, or underground in ducts or directly buried.
||Cu / XLPE / Cu Tape screen / PVC or PE
Cu / XLPE / Cu Wire screen / PVC or PE
Al / XLPE / Cu Tape screen / PVC or PE
Al / XLPE / Cu Wire screen / PVC or PE
Plain annealed Copper or Aluminium, circular, stranded, class 2 per IEC 60228.
||Semi-conductive screen over the conductor, XLPE (cross-linked polyethylene) insulation and Semi-conductive screen over the insulation (strippable 1 ), applie by simultaneous extrusion in just one operation.
|Metallic Screen over each conductor
||Copper wire screen – annealed copper wires helically wound and an equalising copper tape applied in an open counter-helix. Or Copper tape screen – a copper tape, helically applied with overlap. Screened conductors are stranded together with fillers. A Poly Propylene tape is applied over this core
||Extruded PVC or PE.
||Extruded polymeric material.
||Extruded PVC or PE. Optionally, a Low Smoke Halogen Free thermoplastic compound can be used for cables with need for improved fire behaviour.